You can have your boiler installed safely in most rooms, or even the loft. However, you do need to consider the Building Regulations for boiler installation. Your Gas Safe registered installer will be able to help you with this.
- Your boiler should be installed inside a building and can be fitted to any suitable wall strong enough to take its weight when full of water.
- The boiler's flue must be able to pass to the outside, either through an outside wall or through the roof. In the manual you will find the minimum legal distances the flue terminal must be from windows, air bricks, other buildings etc, to comply with the Building Regulations for boiler installation.
- As well as the flue, you must consider where to fit the condensate pipe that takes away the liquid that condenses as the gases cool inside the boiler. We recommend that this pipe discharges internally into the household drainage system. If the condensate pipe is fitted outside, it could freeze during cold weather and make the boiler shut down.
- Our heat only boilers don't require a pump overrun or permanent live. This means you won't need to worry about getting a wire from the pump to the boiler or a permanent power supply to the boiler.
- If you decide to have it fitted in a garage or outhouse, we recommend you get additional frost protection fitted to protect the system pipework, even if the boiler has its own frost protection.
- When positioning the boiler, you must allow sufficient clearances and access for servicing. Please check the installation instructions for details.
- Under certain conditions, the boiler may be fitted inside a cupboard without air vents. Modern boilers are room sealed and will normally run sufficiently cool without ventilation. Please refer to the boiler siting section in the installation instructions to ensure there is enough space in the cupboard for the boiler to be properly installed and serviced.
- If the boiler is fitted in a bathroom or shower room, please refer to the current Wiring Regulations and Building Regulations, which explain the different zones in the bathroom where it is safe to install a boiler, and where it is unsafe to do so. (In GB this is the current I.E.E. Wiring Regulations and Building Regulations. In Republic of Ireland, reference should be made to the current edition of I.S. 813 "Domestic Gas Installations” and the current ETCI rules).
- If your house is a timber framed building, please refer to the current edition of Institute of Gas Engineers Publication IGE/UP/7 (Gas Installations in Timber Framed Housing).
- If your boiler runs on LPG (Liquid Petroleum Gas), you should not have it installed in a basement or other position below ground. This is because LPG does not rise, and will therefore not be dispersed should there be a gas leak.
This information should be used for guidance only.
Your Gas Safe registered installer will be able to survey your home, discuss your installation requirements and tell you the most convenient, safest place that complies with the Building Regulations.